Click on the category below, or if you're not sure use the Search Box in the top righthand corner by typing in some text (e.g. type in "site assessment forms" to find the HERS portfolio site assessment forms; type in ecs to find information on ECS HE version H&S test and ECS card ordering procedure; type in "registering" to find the form for registering an organisation to HERS)
H&S Alert: Cutouts
By Super User
HEA Health and Safety Alert: CUTOUTS
Instances have occurred of the fuse assembly becoming detached within the cutout, and there may be situations when the cutout casing could become live.
Catastrophic failures have been reported at intervals for a number of years – the last one within the last month - and can occur when removing or replacing the cutout fuse carrier. The reason for such failures is not known in every case, but in some cases it has been due to the combination of missing shrouds and insect infestation – with the electricity tracking across the insects causing a direct line to neutral short. In at least one case there does not appear to have been any visible signs of distress or other issues which may have caused the failure.
|File Size:||161 KB|
|Last Updated Date:||04-08-2014|